Scope of Works
A review of the initial DC earth electrode system has highlighted a need to upgrade the system to provide a more robust and lower impedance electrode system for the site.
Six new earth electrodes will be installed along the eastern perimeter of the property, and connected to each other via a galvanised earth strap.
This upgrade will reduce the impedance to earth to approximately one eighth (1/8) of the current system.
No internal changes are required as part of the upgrade works.
** Works refined to include trafficable pits
Works were required to be carried out near buried high pressure gas line.
Ensure system installed is compliant, tested and meets the specified criteria as details in the scope of works.
Manage public and private access around area to adjacent properties and car parks